The topic today of our Modo Pump is coming!
We Modo Pump would like to talk with you the pump assembling today.In order to make the pump a long life,what kind of problem we should consider and avoid it?Please check details as follows:
There are three types of slurry pump layout: open air layout, semi open air layout and indoor layout outdoor. A.The sand slurry pumps arranged in the open air are usually arranged at the lower side of the pipe gallery or near the equipment to be pumped. The utility model has the advantages of good ventilation, convenient operation and maintenance;
B. Semi open air layout. The high pressure multistage pumps arranged in the semi open air are suitable for rainy areas. Generally, the water pumps are arranged under the pipe gallery, and the canopy is arranged on the upper part of the pipe above. Or the pump shall be arranged on the lower floor of the frame, with the frame platform as the canopy. These centrifugal high head pumps can be arranged in single row, double row or row according to the design layout requirements related to pumps.
C. indoor layout In cold or windy areas, the centrifugal water pump can be arranged indoors. If the process requires the equipment to be arranged indoors, the water pump to which it belongs shall also be arranged indoors.
2.Specific requirements for pump layout
A. We Modo Pump arranged the pumps in rows shall be arranged in groups according to the fire protection requirements, operation conditions and material characteristics; when the water pumps are arranged in open air and semi open air, the combustible liquid pumps with the operating temperature equal to or higher than the self ignition point shall be arranged in a centralized way; the fire separation distance between the water pumps and the combustible liquid pumps with the operating temperature lower than the self ignition point shall be no less than 4.5m; the fire separation distance between the pumps and the liquid hydrocarbon pumps shall be no less than7.5m; B. When the water pumps are arranged in rows, it is better to align the center line of the pump end and the inlet, or the foundation sideline of the pump end; 3. When the pumps are arranged in double rows, the power ends of the two rows of multistage water pumps should be opposite, and the maintenance channel should be left in the middle; 4. When the pumps are arranged under or outside the main pipe gallery, the minimum clear width of the channel in the pump area is 2m, the minimum clear height is 3M, and the width of the operation channel in front of the pump end should not be less than 1m;
If you have any question about the pump assembling,welcome to email us!